Item #: 2-3064
Our Price: $48.46
Availability: Usually leaves our warehouse within 1-2 business days
Tecmark Tridelta (TDI) Pressure Switch for electronic Gas heaters used on spas and pools, 3064. SPNO, Normally Open, 25 Amp water pressure switch has two 1/4” standard tab wire terminals, Common and NO. Water connection is made by a 3/16” brass compression fitting (ferrule and nut) included to attach to a siphon loop tube, a brass or copper water tube, commonly used on older gas pool and spa heaters. Tridelta/Tecmark pressure switch 3064 pressure switch, used on electronic gas heaters by Zodiac (Jandy/Laars), Raypak and other heaters using a 3/16” copper water supply line. 1/4” switch is also available, see part number 2-3032./p>
Pressure switches are used on spa, tub and bath heaters to measure the amount of water pressure inside of the heater, as an approximation of water flow. Pressure switches are safety devices intended to prevent heater damage and overheated water hazards. If your pressure switch is causing the heater to shut down, look for causes of low flow in and out of the heater, and remove the spa filter temporarily to improve flow. Pressure switches do fail eventually (which is why sell replacements), but first assume a flow problem, and not a switch problem.
Adjustable Pressure Switch comes factory set but can be adjusted from 1 to 5 psi. Pressure switches do not normally need adjustment after installation, and to avoid heater damage or overheated water, large adjustments should be avoided. 1-2 psi is the correct setting for most spas, tubs and whirlpools. High Altitude locations or spa systems located several feet Below the spa, may need 3-5 psi settings. Refer to your spa heater manual or heater documentation, for any instructions on heater pressure switch settings.
Please Confirm you are not a bot
To customer care-This exceeds my wildest expectations. I did not expect another new cover for the damage inflicted in shipping on my new cover. What I did expect was an explanation how to place some type of patch on it...read more