Item #: 2-3098P
Our Price: $19.52
Availability: Usually leaves our warehouse within 1-2 business days
Tecmark Tridelta (TDI) Pressure Switch for electric heaters used on spas and hot tubs, 3098P. SPST 1 Amp water pressure switch has two 1/4” standard tab wire terminals, Common and NO. 3098P switch has an ABS body and 1/8” NPT plastic threads with a 1/4” long sensor extension below the threads. Note: 1/8” NPT threads to attach the water line or to screw into heater tube or header actually measures 3/8” OD when measured across the threads. Extended sensor prevents this 1/8” pressure switch from fitting many types of heaters, this extended pressure switch is usually mounted in the header or manifold with space to accommodate.
Pressure switches are used on spa, tub and bath heaters to measure the amount of water pressure inside of the heater, as an approximation of water flow. Pressure switches are safety devices intended to prevent heater damage and overheated water hazards. If your pressure switch is causing the heater to shut down, look for causes of low flow in and out of the heater, and remove the spa filter temporarily to improve flow. Pressure switches do fail eventually (which is why sell replacements), but first assume a flow problem, and not a switch problem.
Adjustable Pressure Switch comes factory set but can be adjusted from 1 to 5 psi. Pressure switches do not normally need adjustment after installation, and to avoid heater damage or overheated water, large adjustments should be avoided. 1-2 psi is the correct setting for most spas, tubs and whirlpools. High Altitude locations or spa systems located several feet Below the spa, may need 3-5 psi settings. Refer to your spa heater manual or heater documentation, for any instructions on heater pressure switch settings.
Please Confirm you are not a bot
Just wanted to say thank you, our new cover arrived today. It looks and fit great. I was a little nervous ordering something like that over the internet, but your site made it easy and delivery was right in the...read more